Our installation at a barn conversion. This is the first time the property has had a water supply.
The nearby spring was diverted into a buried water tank, which then overflows to continue feeding the properties further down the valley.
The water analysis showed failures on pH at 5.2, Iron at 500µg/l and coliform bacteria.
A dry run protected, stainless steel well pump was installed in the tank controlled by a pressure switch with a pressure vessel.
The treatment includes a backwashing filter vessel with a mixed media to elevate the pH and remove the iron. After this a long life cartridge filter and high flow UV steriliser, for bacteria control, are installed.
The water test carried out by Springbore after completion shows a pH of 7.4 and the iron level at <100µg/l.